Smoke dampers are not required in fully ducted systems. Smoke dampers are required in systems that are not fully ducted and the duct penetrates a smoke barrier. Smoke dampers are also required where an air transfer opening penetrates a smoke barrier.
What are the locations that smoke dampers are required in existing healthcare that are protected by an approved, supervised automatic sprinkler system with quick response sprinklers?
View all comments